The PAP-R Series: Offering One Rank Up in High Precision Air Processing
Integrated Design Saves Space and Eases Installation
Convenient All-In-One Design
Previous Air Processors
Each component takes up valuable space.
PAP-R Facility-Use Precision Air Processor
All-in-one design saves space and makes installation easy.
Energy Saving Example
Power Consumption Comparison of Precision Air Processors for Constant Temperature Chamber, Constant Temperature and Humidity Chamber, Clean Room
Optional Equipment and Parts
For Precision Air Processing Applications in Every Field
ORION has many items in addition to the optional equipment shown below to suit our users' environment, needs, and demands. Please feel free to contact your dealer with any questions.
Plenum Chamber with HEPA Filter
Rear Intake Unit
Outdoor Unit Wind Shield
Front Intake Noise Reduction Chamber
・Plenum Chamber with HEPA Filter Assembly
・Plenum Chamber Assembly
・Rear Intake Unit Assembly
・Front Intake Noise Reduction Chamber Assembly
・OA Set Assembly
・Outdoor Wind Shield Assembly
・Drain-Up Unit (Incl. PVC Piping Kit)
・Sensor Mounting Bracket Assembly
・Humidification Unit Water Supply and Drainage Coupling Set (For PAP20A-KR and PAP40C-KR models)
・Condensation Piping Set
・Base Cover Plate Set
・Remote Control Cord Assembly (50 m)
・Remote Control Cord Assembly (100 m)
・Communications Software Set
・Cleanroom (Pharmaceutical, Cosmetic Production Etc.)
・Precision Measurement Room (3-D Measurement Instruments, Tensile Testing Equipment, Laser Measurement Instruments, etc.)
・Precision Processing Room (Nano Processing Equipment, Electrical Discharge Machines, etc.)
・Storage of all kinds of Materials...etc.
・Plant Cultivation Room / Plant Factory...etc.
Every kind of system that meets our users demands.
System Installation Examples
① Outlet Control Method (±0.2 to 1 ℃)
② Intake Control Method (±0.5 to 2 ℃)
Constant Temperature and Humidity Chamber [Set Temp/Humidity: 23 ℃ / 50% year-round control]
Built-in design (fitted inside insulation panels) making the air processor flush with the wall providing an effective use of space.
*1 The temperature and humidity control range noted does not necessarily indicate the actual controllable range possible.
The range of control depends on the condition of the air supplied at the intake.
*2 When the intake air temperature and humidity, and outdoor ambient temperature are stable. Noted precision is based
on measurement by the internal controller at a single air outlet point.
*3 When operating according to JIS B 8616.The displayed performance will be at least 80% when the intake air
temperature of the outdoor unit is at least 35 ̊C.
*4 When operating according to JIS B 8616.The displayed performance will be at least 75 % when the intake air
temperature of the indoor unit is below 20 ̊C. The compressor will stop, and exclusive operation of the auxiliary heater
may occur if the control air intake temperature drops to approx. 15 ̊C or lower.
*5 The noted external static pressure is when the controlled air is regulated at the outlet to produce the maximum rated
processing air flow.
*6 External dimensions do not include miscellaneous protrusions such as eyebolts, etc.
*6 Maximum value within the range of unit specifications. Starting current is equal to or less than the operating current.
*7 The figure noted is when the equipment is operating at the highest level of humidification operating at the highest
capacity of its normal operating range.
*8 Source voltage phase unbalance should be less than ±3%.
*9 Maximum value within the range of product specifications.
*10 The figure noted is when the product is operating at the highest capacity of its normal operating range.
*11 Measured value (A scale) when operating at the rated processing air flow, at a position of non-resonance, 1 m from
the front face of the indoor unit, and at 1 m from the front face of the outdoor unit, at a height of 1.5 m.
*12 Blower fan output cannot be increased.
*13 Use the measured temperature and humidity bias function to correct any error between the temperature and humidity
shown on the control panel and the user's measured temperature and humidity.
Note 1: This product does not detect electrical shorts and does not have a protection function against them. An earth
leakage breaker must be installed on the primary side of the power supply.
Note 2: All ducting should be insulated and ducting length should be kept as short as possible. (5 m or shorter